Overhead Insulated Power Cable
This product is made in accordance with the standard of GB/T 12527-2008 Overhead Insulated Power Cable with Rated Voltage of 1 kv or below.
1. Rated voltage U is 1 kv or below.
2. Allowable maximum long-term operating temperature of the cable conductors:
PVC insulated and PE insulated powers cables should not exceed 70 ℃.
XLPE insulated power cables should not exceed 90 ℃.
3. Cable laying temperature should be no less than -20 ℃.
4. For cables with an outer diameter (D) of less than 25 mm, their bend radius should be no less than 4D.